A Doubleview customer sent us this picture of his submersible pump and 3 phase motor. He and his electrician had pulled it out of his very old 32 metre submersible bore hole. They had disassembled it and electrically tested the motor.
The motor needed replacing. We attended and replaced the motor and while we were at it a new submersible pump. We replaced all down hole electrical cable which we heat shrunk to the new motor lead. We also replaced his old frayed stainless steel draw-wire but reused the existing 40 mm poly rising mainline that delivers the water. The poly pipe was all good even after several decades of service. At the same time we dosed the bore with 20 litres of chlorine to help kill the iron oxide bacteria that was evident.
Finished off with a new bore box at the bore head, reconnected and all set to go. Most Doubleview water bores are in the 30 to 60 metre deep range as a consequence of Doubleview’s elevation. If you have any questions call our team on 9246 0111.