If you have a water bore and have white sand coming from your sprinklers call us on 9246 0111.
You’re never meant to see white sand coming from a sprinkler. In the case of this customer they had an old style well.
The screen had failed which allowed in sand. It is very white sand that comes from water bearing ground that is washed almost iridescent over the years. The options for this broken Perth water bore was to either redrill a spear into the existing well or drill a new submersible bore.
After assessment by our bore serviceman it was decide it was more economical to opt for a new modern submersible water bore. Our bore installation and service team at can help with any bore problem in Perth. Call us on 9246 0111 or you can book a bore service HERE .
Last week our water bore drilling team drilled a water bore in a very difficult to access site in Cottesloe.
The front wall had already been built and there was no other way to back our drilling rig onto the property as the carport extended out to the footpath. We backed our drilling rig up to the low front wall so the platform overhung it. We then jack hammered out the footing of the wall and then drilled our 20 metre deep water bore in the raised garden bed.
With the mild salinity concerns in Cottesloe we are always cautious not to drill too deep here. The fresher water is less dense then the more saline water and consequently ‘floats’ on top.
Call our installation division Virgin Bores on 9246 0111 or visit our main website www.virginbores.com.au
If you would like a modern submersible water bore or a new reticulation system in the Noranda area call 9246 0111.
We drilled a new submersible garden water bore here last week at this house in Noranda, now we have installed a new reticulation system. With the extra flow from the bore versus mains scheme water, we were able to run pop up sprinklers for the lawn on one station and separate micro sprays for the garden beds on another. The half sprinklers that face the house backing onto the curb are prone to car tyre damage. So we installed come concrete surrounds to this line of sprinklers and those on the edge of the driveway to protect this new Noranda reticulation system.
With the installation of a modern submersible water bore, the client is now able to use their sprinkler system three days a week instead of only two days allowed from mains water. This Noranda front garden is about to have a new lawn laid. They will be able to apply for a new lawn exemption and water the new lawn more often details here
While we were there, we popped our head over the side fence and took a look at the neighbor’s garden. We drilled new submersible water bore at the property last year and their garden looked great. We are very happy to get referrals from happy customers.
If you live in the Noranda area and would like to discuss a new water bore or reticulation system call us on 9246 0111 or check out our website HERE
Our reticulation mobile service teams cover the Perth metropolitan area so if you need a new reticulation controller we can help you promptly, simply call 9246 0111.
We carry parts and can replace your reticulation controller whether it is hard wired or it is a plug pack model that is plugged into a power point. We can replace reticulation controllers that run mains water or water from a submersible water bore. Pictured are a coupe of types of retic controllers but there are many available we can talk you through.
If your Perth reticulation controller needs replacing call us on 9246 0111 with details of your controller and we can give you an idea of a fully installed replacement.
We installed a new submersible water bore for a client who knew there would be problems with access for the water bore drilling rig. All suburbs 9246 0111.
We couldn’t use any of our portable or smaller drilling rigs because the ground was mainly limestone. We knew from experience the limestone would go all the way down to his required depth of 28 metres and it needed the power of our truck mounted drilling rigs to be drilled successfully.
There were large brick walls around the entire property so the only option was to drill the bore in his driveway. Normally a simple job to drill a bore in a driveway if it is paving. Then we simply lift pavers, drill the bore, install and connect the submersible pump and then replace the pavers. But this driveway was poured aggregate. Customer was determined to get a bore. Solution…we arranged a contractor to cut a neat circular hole in the aggregate driveway.
We preserved the circular cut out. After bore drilling and installation this same cut out plug shown here was put back as the lid over our bore box.
It was a very neat solution. Ring us with your Perth water boring challenge on 9246 0111 or read more about getting a modern submersible water bore here.
We often get water bore repair calls where the problem turns out to be the start capacitor. Call on 9246 0111.
In a single phase submersible bore pump the start capacitor is ordinarily in the 240 volt start box. Three phase submersible pumps do not have start capacitors. In some centrifugal pumps the capacitor can be mounted externally on the pump motor housing. It is surprising how often a faulty capacitor is missed as the cause of a bore pump problem particularly when tests are carried out by someone who is not specifically experienced in bore pump service work. Even trained general electricians can misdiagnose this simple problem.
Often a capacitor problem can spotted visually as it will commonly swell or rupture. A start capacitor should be perfectly cylindrical. Sometimes though a faulty capacitor can only be diagnosed by the serviceman actually testing it when disconnected. As the start box is mains powered it does need a licensed electrician or certified electrical worker to test and replace the start capacitor. Our specialist bore electrician Dave is expert at this.
One of our clients from Baldivis sent us these pics of inside his submersible water bore start box.
This is a single phase start box and is a particularly dramatic example of a blown start capacitor.
Our mobile bore service teams carry a variety of different size start capacitors and can quickly diagnose and fix this common bore problem. We repair water bores in all Perth suburbs, call us on 9246 0111 or book a service online
Our specialist bore electrician recently fixed a circuit breaker that was tripping in Beechboro. Call 9246 0111.
Dave, our electrician, tested the single phase submersible pump and all the electrical tests were OK but were marginal on this Beechboro water bore.
There was an old metal start-box which was rusted out and dangerous. He replaced and rewired the start box with a new 1.5 kw rated box with matching start capacitor. Dave replaced some dangerous connections at the bore head and retested everything. Given the apparent age of the submersible pump it will likely need replacing in the next few years. We have recommended that at that time the down hole electrical cable and stainless steel draw wire is also replaced.
Dave is an excellent bore electrician and ask him why one of our customers called him a “little treasure”
We have a wealth of experiencing servicing bores and pumps throughout Perth. Give us a call on 9246 0111 or visit HERE for more information or if we can help you.
Our mobile service teams do prompt repairs to ALL TYPES of Water Bores & Reticulation Sprinkler Systems Perth metro-wide. Free phone advice. Our experience saves you time and money. Bore repair HOTLINE 1300 734 300 North of River: Troy 0408454130 South of River: Brett 0411511611