If the pump is not starting at all
- check the fuse or circuitbreaker that should be in your meter box and labelled “bore” or “pump”
- if it is 3 phase reset the 415-440v D.O.L ( Direct Online Starter)
- if it is single phase there is most likely a separate 240v start box with a reset/over-ride switch, check that
- if it is operated from a reticulation controller check that that has 240v power going to it. Just because the reticulation controller has a display does not mean it has 240v power. Remove the 9v back up battery and confirm there is still a display.
- can you hear the 24 v relay clicking in or the contacter make a clunk sound when you start the retic contoller? Starting the reic controller sends a 24v signal to a relay or contactor which turns on the “mains” power to the bore pump.
- if all the above seems OK and it is a submersible pump, perhaps the motorit is starting and you can’t hear it but another related water delivery problem exists. Does your electricity meter speed up when you start the pump?
- if it is a centrifugal pump in a well have you checked the isolation switch?
Call us on Perth 1300 734 300 if none of the above helped. We may be able to help further on the phone or we will send our mobile bore service teams to any Perth suburb. Further info is on our main website.
Thanks for visiting our Blog. Water Bores and Perth Groundwater are our passion. If your water bore is broken we can fix it!
From Lancelin all the way down to Mandurah our service teams are ready to help. We repair both modern submersible bores and the old well-liner type. From blown fuses to bores running out of water, we can help. Because we specialize in water bore repairs we are Perth’s number 1 callout mobile service to repair bores. No need for a multiple of trades and the delays in between getting an electrician and then a pump man. We can send our bore electrician first off if it is an electrical problem then we can fix there and then if simple or follow right through to pump replacement if necesary. Call us on 1300 734 300 for prompt metro-wide service.
Water Bore not working?
If you have a bore problem of any type in the Perth metropolitan area, call us 7 days a week. 1300 734 300
If it is fixable we can fix it!
Phone: 1300 734 300. You are reading our blog or you can choose to Visit our Website
We repair or replace all brands of submersible bore pumps. Some of the more well known brands or stampings are Lowara, Grundfos, Franklin, Universal, Davey, Red Jacket, Orange, Sumoto, Arwana, Centripro, Marlow, Pioneer, Onga, B & L and Coverco.
Sometimes it is confusing when different terms are used when describing submersible pumps and some industry jargon can be understandably hard for the novice to decipher. Talking about domestic stainless steel submersible pumps in Perth we are normally referring to 4″ pumps ( designed to fit inside a 100mm borecasing). What is collectively referred to us the pump is actually two distinct and separate parts. The electric motor ( single or 3 phase) and the wet-end (or pump) which is the series of impellors. Both these parts bolt together and are almost always brand interchangeable i.e each brand fits together with each other.
Call us on 1300 734 300 for further info or help. We repair pumps and bores all over Perth.
Today our service hotline received an urgent Saturday afternoon call from a lady in South Perth. “My sprinklers won’t turn off”.
We asked a few questions and although her reticulation system wasn’t fed from a bore we sent a serviceman anyway to help her out. There was only one station on her retic system connected directly to mains water and that solenoid valve had failed. The only way she could stop the water was turn the entire supply off at the water meter. We replaced the faulty solenoid valve and whilst we were there installed a manual gate valve so she could easily isolate the sprinkler system if ever the problem happened again. Another happy customer.