Don lives in Bibra Lake and the new pump in his old well was not pumping water.
He had rung several companies and it seems all they saw was $$$.
He then rang Brett, who started Virgin Bores nearly 20 years ago, and is very knowledgeable about most things that can go wrong with a bore or old style well.
Brett talked through with Don over the phone how to prime his pump. It took a lot of water to top prime but it worked on the third attempt. Although there wasn’t much water coming out at first once the pipes had filled at the front and back of the house the pump changed sound and was really working.
Don told us that if he had any future problems or repairs he would call Virgin Bores on 9246 0111.
Don, thanks for the great review. We always try and put the customer first. If we can help you with repairs to your older style call us for expert advise on 9246 0111.
A resident of South Perth was concerned as their reticulation was not working and they contacted us on 9246 0111.
They reported that they could hear the typical “çlunk” sound as the contactor engaged when they started the bore pump from their retic controller.
Our electrician found that the one horsepower Sumoto submersible motor was not fused. The motor windings appeared to be intact but there was a complete dead short to earth.
His recommendation was that we replace the submersible motor, wet-end and electrical cable down the bore hole for new. He disabled and taped up motor tails in the borehead junction box and all the other electrics tested OK.
So another member of the team returned and replaced the .75KW submersible motor, 15 metres of electrical and stainless and barrell union. All tested OK and another South Perth water bore was back up and running for the hot summer months ahead.
When there is a problem with a water bore it takes experience and skill to diagnose the problem and repair efficiently, quickly and economically for the Perth householder.
We have been repairing Perth water bores for 20 years and have been faced with most problems when repairing a water bore, Call us on 9246 0111 or book a bore service here
A modern submersible water bore saves money and is normally low in maintenance.
If something does go wrong with your water bore, call us on 9246 0111 and we will help you fix it and be ready for the hot summer months in Perth.
Dave from Hocking called us because his bore was tripping. We sent our Dave, the electrician, to test the 1.5 kw submersible motor. It tested OK. The pump was also running OK but after a while the start box overload tripped so Dave bypassed the faulty overload.
Also there were 6 programs with 6 start times in each, now there is only one program with one start time. The reticulation now comes on Wednesday, Friday and Sunday at 6 am for 10 mins on the 7 stations.
So Dave’s sprinklers are now coming on and he is all organised for summer.
So if you are in Hocking or the surrounding areas of Wangara or Wanneroo and your water bore needs fixing call Troy on 9246 0111 or book an online service HERE
Our bore electrician Dave attended a bore service job in East Fremantle to repair a water bore reported electrically failing.
The water bore is approximately 50 metres deep with a 1.5 kw Sumoto submersible motor. Dave reported the motor tested OK.
However, the start capacitor in the bore start box was completely blown and part of the start box was melted. So Dave replaced 50MF capacitor for new. He then ran the bore and retic and tested and it was all working OK. Note the ruptured start capacitor. The grey ” gunk” oozing out is typical when a capacitor swells and bursts. This one had burnt and blown more than we normally see. Our customers had smelt the burnt odour walking past the bore control box.
If we can help you with a broken water bore in the East Fremantle, Bicton, Palmyra or surrounds call 9246 0111 or book a bore service online.
Our mobile service teams do prompt repairs to ALL TYPES of Water Bores & Reticulation Sprinkler Systems Perth metro-wide. Free phone advice. Our experience saves you time and money. Bore repair HOTLINE 1300 734 300 North of River: Troy 0408454130 South of River: Brett 0411511611
You must be logged in to post a comment.