A resident of South Perth was concerned as their reticulation was not working and they contacted us on 9246 0111.
They reported that they could hear the typical “çlunk” sound as the contactor engaged when they started the bore pump from their retic controller.
Our electrician found that the one horsepower Sumoto submersible motor was not fused. The motor windings appeared to be intact but there was a complete dead short to earth.
His recommendation was that we replace the submersible motor, wet-end and electrical cable down the bore hole for new. He disabled and taped up motor tails in the borehead junction box and all the other electrics tested OK.
So another member of the team returned and replaced the .75KW submersible motor, 15 metres of electrical and stainless and barrell union. All tested OK and another South Perth water bore was back up and running for the hot summer months ahead.
When there is a problem with a water bore it takes experience and skill to diagnose the problem and repair efficiently, quickly and economically for the Perth householder.
We have been repairing Perth water bores for 20 years and have been faced with most problems when repairing a water bore, Call us on 9246 0111 or book a bore service here