A customer in Dalkeith rang us on 9246 0111 after their three phase submersible bore was tripping their 3 phase circuit breaker and they were not getting water from their garden bore.
We have an expert specialist bore electrician (Dave) who was the man for the job. He found that the three phase submersible motor was instantly tripping the three phase circuit breaker in the meter box when the retic was turned on.
Dave meggar tested the pump motor at the borehead sending a current down hole to the motor. Pump motor tested fine. What he did find was burnt out wiring in the junction box ( pictured below) contained in the green box at the top of the submersible bore hole. He replaced the junction box and all is working well now. Whilst there Dave tested the reticulation system to make sure there were no other faults.
A modern submersible water bore can save you thousands of dollars. So if you don’t have a water bore or your water bore needs repair call us on 9246 0111 or find out more HERE
You must be logged in to post a comment.