James from Mount Pleasant phoned regarding his submersible pump that was tripping the circuit breaker. (Call us anytime on 9246 0111 if you need help too)
The water bore was drilled in his driveway and it was very useful to know that the paver to show where the bore was located was a different color. As pictured the bore head was was covered by an old concrete lid pit.
Our senior experienced bore electrician Dave reported the motor was about 8 years old. The 1.1 kw 2 wire subbie motor was dead short to earth and although the motor’s windings appeared to be intact the internal capacitor had ruptured. So we replaced it with a new 1.1 kw sunbmersible pump motor and replaced the start box and junction box.
We have drilled and repaired many water bores in Mt Pleasant, Applecross, Bateman Ardross and surrounds. We are very experienced with the conditions in the area. If your water bore or retic is in need of repair call us on 9246 0111 or check out our main website HERE